The generator for the new side of the jail failed to operate both manually and automatically as required after the main power source to the jail was
During the walk through, this inspector observed that the fire panel was
showing trouble and would not reset to normal mode. The fire alarm panel is not safe, secure and fully operative as required by minimum standards. Until the repair is completed, a 15 minute fire watch will be conducted on the new side of the facility.